|Barrier # New||Building Name||Room No.||Space Name||Item / Component||Barriers||ADA Standards and Regulations||BIDMC Action to Comply with the ADA|
|194||Feldberg||2nd floor||Cashier||counter||mounted too high||4.1.6(1)(b), 4.1.1(2), 7.2(1)||Install compliant counter or add auxiliary counter|
|195||Feldberg||FD-678||Toilet Room in OB/GYN Dept||side grab bar||incorrect placement||4.1.6(1)(b), 4.1.3(11), 4.22.4, 4.16.4||reposition|
|196||Feldberg||FD-678||Toilet Room in OB/GYN Dept||shelf above toilet||high||4.1.6(1)(b), 4.1.3(12)(a), 4.25.3||relocate/remove shelf|
|197||Feldberg||FD-778A||Patient Room Shower||side grab bar||incorrect length||4.1.6(1)(b), 4.1.3(11), 4.21.4, 4.23.8, 4.26, Fig.37||install compliant grab bar|
|198||Feldberg||FD-778A||Patient Room Shower||hook||above reach range||4.1.6(1)(b), 4.1.3(12)(a), 4.25.3||reposition or add hook|
|199||Feldberg||FD-778A||Patient Room bathroom||toilet paper dispenser||incorrect placement||4.1.6(1)(b),
4.1.3(11), 4.23.4, 4.23.7,
|200||Feldberg||FD-778A||Patient Room Shower||paper towel dispenser||protruding object||4.1.6(1)(b), 4.1.3(2), 4.4.1||reposition
|201||Feldberg||FD-778A||Patient Room Shower||shower curb||shower has curb||4.1.6(1)(b), 4.1.3(11), 4.23.8, 4.21.7||provide accessible shower|
|202||Feldberg||7th Floor||Outside Oncology||telephone||above reach range||4.1.6(1)(b), 4.1.3(17), 4.31.3||provide accessible house phone and directional signage|
1. Per paragraph 20 of the Settlement
Agreement, corrective measures to newly constructed facilities noted herein
shall comply fully with the New Construction provisions of the ADA, 42 U.S.C.
§ 12183(a), 28 C.F.R. §§ 36.401 & 406 including the ADA Standards for
Accessible Design, Appendix A.
3. ADA Standards for Accessible Design define medical care facilities as those in which people receive physical or medical treatment or care and where persons may need assistance in responding to an emergency and where the period of stay may exceed twenty-four hours. In addition to the requirements of 4.1 through 4.35, medical care facilities and buildings shall comply with 6.
Cases & Matters by ADA Title Coverage | Legal Documents by Type & Date | archive.ADA.gov Home Page